The NY-100 New York module provides three separate functions. A Manual Trip switch for activating the Auxiliary Alarm Contacts. A Fan Purge enables key switch and a Fan Shutdown reset key switch.
The NY-100 contains a Manual Trip switch used to activate the LSN 2000 Auxiliary Alarm contacts (Aux Alm). These contacts are generally used to notify a Central Office company the fire alarm system is in alarm. The Manual Trip switch works whether power is applied to the Fire Command Center or not. A red protective cover to prevent accidental tripping is supplied.
The Fan Purge enables key switch prevents fan controls from being issued until the key switch is turned from the DISABLE position to the ENABLE position. The key switch is keyed with the NYC Fire Department 1620 cylinder. The Fan Shutdown reset switch prevents fans that have been automatically shut down due to a fire condition from restarting after the alarm condition has cleared. To restore fans to their normal position after the alarm condition has cleared, turn the Fan Shutdown switch from the NORMAL position to the RESET position. No field wiring is required.
- Microprocessor Controlled
- Manual Trip Central Office Switch
- Fan Shutdown Reset Switch
- Fan Purge Enable Switch
- Low Power Consumption
- 1/2 Module Footprint
- No External Field Wiring